Landings, corridors and general association areas can need high levels of illumination during the day, which may not be required at night. Daylight harvesting, separate switching of luminaires, dimming or presence detection can be used to reduce energy usage.
Please move your cursor through the illustration and click on the blue squares for more information about recommended products for Association Areas.
Best Practice Advice
Energy Saving LED Upgrades
If lighting controls can not be used, to modify lighting levels and reduce energy consumption, then upgrading to LED lighting can instantly save energy.
Custodial luminaires with a removable internal gear tray enable quick and simple technology upgrades, without the expense and inconvenience of replacing an entire light fitting.
Avoiding a “Logistical Nightmare”
In a custodial environment moving prisoners to other locations, so that building work can be undertaken, can be a logistical nightmare.
By quickly and simply upgrading existing luminaires to LED, utilising replacement gear trays, the installed lighting will use less energy and run for longer – reducing ongoing maintenance.
Specific Lighting Requirements
Association areas are usually supervised. However luminaires with high IK and IP ratings prevent physical attack or the luminaire being used as a weapon. “Low flicker” is also an important requirement as it is likely CCTV will be used in these areas.
Association areas may also need to incorporate emergency lighting. For more information CLICK HERE.
In association areas, just as with other custodial applications, lighting must be physically robust, tamper resistant and built in such a way that items cannot be hidden within them. As a minimum, we would recommend an IP rating of IP54. Lighting needs to be of good uniformity and a minimum of 200 lux. When illuminating stairwells, consideration should be given to contrast between adjacent areas and surfaces.
As prisoners can congregate together in areas such as walkways, landings and stairs it is a requirement that fixtures are not capable of being used as weapons. Lighting should be securely mounted to the wall, and tamper proof screws incorporated to prevent prisoners from exposing live parts.
For further lighting advice speak to our technical sales team on 020 8254 2022.
Why Choose Designplan?
PDF Lighting Guide
Our 24 page lighting guide identifies typical custodial applications, focusing on the principles of good lighting. We examine the benefits of robust construction, standards compliance and specific design requirements including anti-ligature luminaires for “safer” cell applications. To download your copy click on the button below.